Building Automation System Medical Gas System BACnet Integration
- Network accessible I/O with built-in 10/100 Mbps Ethernet port
- Supports BACnet/IP
- Adheres to BACnet Application Speci c Controller (B-ASC) pro le
- Supports up to 30 master alarm inputs
- Low-voltage 24 VAC or VDC powered LED indicators for inputs, outputs, CPU status, and Ethernet activity/link/data rate
The BACnet Interface Module provides a convenient method of interfacing Amico Master Alarm to building automation systems that utilizes BACnet technology.
The BACnet interface complies with BACnet/IP as de ned in ANSI/ASHRAE Standard 135-2004
The BACnet Interface Module is composed of a 3rd party
BacNet devices wired and con gured to translate dry-contacts signal from Amico Master Alarm panel to a Bac- Net/IP format which can be access with any BacNet/IP server.
The BACnet system can handle up to 30 master alarm points, each 10 pts master board needs one computer interfaceto communicate from Master to BACnet device.
Input power is 115 VAC to 220 VAC, 50 to 60.